Electrical cabinet for 120VAC and Low Voltage equipment.
Available in two sizes:
Surface or flush wall-mounting.
Front vented cover.
Pre-drilled for CBNA-200-Z4
15A outlets for 120VAC distribution.
Ideal for residential and commercial applications.
Front vented panel provides heat dissipation.
16- gauge cold rolled steel.
Dimensions & Weight
|Enclosure||Dimensions(Imperial)||Dimensions (Metric)||Weight (lbs)||Weight (kg)|
|4x2||64” x 30-3/8” x 4-1/16”||162.56 x 78.23 x 10.16 cm||75.00 lbs||34.00 kg|
|4x1||64” x 15-3/8” x 4-1/16”||162.56 x 39.12 x 10.16 cm||43.00 lbs||19.50 kg|
|2x1||36” x 15-3/8” x 4-1/16”||91.44 x 39.12 x 10.16 cm||25.00 lbs||11.36 kg|
Maximum Weight Capacity
|15A duplex outlet||06||03||03|
|Steel junction box||06||03||03|
|Junction box cover||06||03||03|
Mounting The Enclosure
Enclosures must be solidly installed in dry well vented environment; may be flush mounted or surface mounted.
Surface mounted enclosures should be installed on a ¾’’ plywood reinforced wall. Flush mounted enclosures need to be affixed between stud bays. For best results, 5/8in. (16mm) drywall is preferred.
Refer to maximum weight capacity.
Consult our website for driver measurements and weight.
Enclosures are intended for indoor use only. Dry location only.
Enclosures house equipment that requires to be air-cooled, mount in a well-ventilated area.
The ambient temperature range is 32°F to 104°F (0°C to 40°).
The relative humidity range is 10% to 90% (non-condensing).
Allow adequate clearance in front of the vented cover for servicing and ventilation.
ALL POWER FEEDS MUST BE PROTECTED BY A DEDICATED 20 AMP CIRCUIT BREAKERS, SUPPLIED AND INSTALLED BY CERTIFIED ELECTRICIANS IN ACCORDANCE TO LOCAL AND NATIONAL ELECTRICAL CODES.
Enclosure must be wired by a certified low voltage installer in accordance with all local codes.
Enclosure should be grounded as per local and national electrical codes.
Never load electrical breakers at more then 80% capacity.
Calculate AC amperage consumption to determine appropriate electrical requirements and electrical distribution in each enclosures.
Use 12/2 cable for external electrical distribution.
Use copper conductors only – rated at 60°C.
Low voltage and AC should be run within the enclosure separately.
If more then one circuit is necessary in a same enclosure, use same electrical phase.
Equipment power consumption
Power Supply Usage @ 80%
|WATTS||DC AMP||AC AMP|
Refer to our website for specifications regarding maximum weight capacity.
Keep AC separated from low voltage using our included bracket lacing.
Use provided nylon grommets to protect any wires from damage at top and bottom of enclosure.
Leave space between drivers for aeration purpose.
Colorbeam Lighting offers in-factory system configuration and / or assembly should alternate UL certified configurations be required.
Contact Colorbeam Lighting for applicable fees.